To lay down a procedure for preventive maintenance of water chiller for blister machine.
This procedure is applicable for maintenance of water chiller for blister machine.
4.1 Before start of the activity, switch ‘Off’ the power supply and display under maintenance label.
4.2 Switch ‘On’ the main power supply and start circulation pump. Check for any
abnormal sound and overhaul if required, also check motor bearing, in case of abnormal sound replace its bearing. After verification switch ‘Off’ the power supply.
4.3 Check the circulation pump frame assembly and foundation nut-bolts. Tighten them if found loose and replace with new ones if required.
4.4 Check and clean condenser coil and fins with compressed air.
4.5 Check the thermal relay of pump, if found faulty replace it.
4.6 Check for any leakage from tank, rectify if leakage found.
4.7 Check the refrigerant piping, condensing unit for leakage by using soap solution, rectify if leakage found.
4.8 Check calibration status of temperature sensor and temperature controller.
4.9 Check integrity of switches, push buttons and other electrical accessories in control panel.
4.10 Check the panel wiring for any loose connections, if found loose tighten it.
4.11 Before switching ‘On’ the machine ensure water level is proper and copper chilling coil is fully immersed. Add water if needed.
4.12 Remove the under-maintenance label and switch ‘On’ main power supply.
4.13 Take trial run of the unit.
4.14 Record the observation in annexure.
4.15 Preventive maintenance shall be performed at least once in six months.
SOP: Standard operating procedure.
Copyright Notice: This Article/SOP/Compilation/Published Content is protected by Indian & International Copyright Laws. Reproduction and Distribution of the same without written permission is prohibited. Mail us at: firstname.lastname@example.org
For any Feedback or suggestion mail at: email@example.com
Weblink – https://pharmastate.com/